The excitation system of a synchronous generator is a critical component that ensures the generator produces and maintains the desired voltage and reactive power output. It consists of various components and control mechanisms that work together to regulate the generator’s field current, thereby creating a stable and consistent magnetic field in the rotor.
The excitation system of a synchronous generator typically includes components such as the exciter, automatic voltage regulator (AVR), voltage transformer, current transformer, power amplifier, field winding, and rotating diodes.
Each component performs a specific function in the excitation system of a synchronous generator to maintain the generator’s electrical parameters within acceptable limits.
Components of Excitation System of a Synchronous Generator
Let’s now discuss the individual components of the excitation system of a synchronous generator:
Exciter: The exciter is a small generator that supplies the initial field current to the rotor winding. It can be either a separate machine called a separate exciter or a self-excited machine called a self-excited exciter. The exciter output voltage is regulated by the AVR.
Automatic Voltage Regulator (AVR): The AVR is a control device that continuously monitors the generator’s terminal voltage and adjusts the field current to maintain a constant output voltage. It compares the actual voltage with the desired setpoint and adjusts the exciter field current accordingly.
Voltage Transformer: The voltage transformer steps down the generator’s terminal voltage to a suitable level for the AVR and other control circuits. It provides a feedback signal to the AVR to compare the actual voltage with the desired value.
Power Amplifier: The power amplifier amplifies the output signal from the AVR and provides the necessary power to the field winding. It ensures that the field current reaches the required level for the generator’s operation.
Field Winding: The field winding is the rotor winding of the synchronous generator. It carries the field current, which creates a magnetic field when supplied with direct current. The magnetic field interacts with the stator winding to generate electricity.
Rotating Diodes: The rotating diodes, also known as slip rings and brushes, are used to transfer the DC field current from the stationary excitation system of a synchronous generator to the rotating field winding of the rotor.
Working Excitation System of a Synchronous Generator
The working of the excitation system of a synchronous generator can be explained as follows:
The automatic voltage regulator (AVR) continuously monitors the generator’s terminal voltage and compares it with the desired setpoint. If there is a deviation, the AVR adjusts the exciter field current accordingly.
The exciter, whether a separate exciter or self-excited exciter, generates a small amount of initial field current. This current is regulated by the AVR.
The voltage transformer steps down the generator’s terminal voltage to a suitable level for the AVR and other control circuits. It provides a feedback signal to the AVR for voltage regulation.
The AVR compares the actual voltage and current feedback signals with the desired values and adjusts the excitation system accordingly. It regulates the field current to maintain a constant output voltage and reactive power.
The power amplifier amplifies the output signal from the AVR and provides the necessary power to the field winding. It ensures that the field current reaches the required level for the generator’s operation.
The field winding carries the field current and creates a magnetic field when supplied with direct current. This magnetic field interacts with the stator winding to generate electricity.
The rotating diodes, slip rings, or brushes transfer the DC field current from the stationary excitation system to the rotating field winding of the rotor.
methods used in excitation systems
There are several methods used in excitation systems of synchronous generators. Some of the common methods are:
Self-Excitation: In this method, the exciter is connected to the generator’s rotor winding, and it generates the required field current using residual magnetism. Once the generator starts producing power, the exciter feeds back a portion of the generated power to maintain the field current.
Permanent Magnet Excitation: In this method, permanent magnets are used in the rotor to create a magnetic field. The permanent magnets eliminate the need for a separate exciter and its associated control system.
Brushless Excitation: This method eliminates the use of brushes and slip rings by employing a rotating rectifier assembly. The AC output of the main generator is rectified on the rotor, and the resulting DC current is supplied to the field winding.
Static Excitation: In this method, the excitation system uses solid-state devices such as thyristors or silicon-controlled rectifiers (SCRs) to control the field current. It offers precise and fast control over the excitation system.
Final Thoughts on Excitation Systems
The excitation system is crucial for maintaining the stability of the generator’s voltage and reactive power output. It ensures that the generator remains synchronized with the power system and contributes to the overall grid stability.
Failure or malfunction of the excitation system can lead to voltage instability, reduced power quality, and even generator tripping. Therefore, regular maintenance and monitoring of the excitation system are necessary to prevent potential issues.
Modern excitation systems excitation system of a synchronous generator often incorporate advanced control algorithms and digital signal processing techniques for enhanced performance and accuracy. These systems can respond quickly to changes in load demand and provide precise voltage and reactive power control.
Excitation systems are designed to operate under various operating conditions, including steady-state, transient, and dynamic conditions. They must be able to withstand short-circuits, sudden load changes, and other disturbances without compromising the generator’s stability.
Excitation systems play a crucial role in supporting power system stability and control. They can provide reactive power support, voltage regulation, and contribute to grid synchronization during system disturbances or contingencies.
The development of excitation systems excitation system of a synchronous generator has seen advancements in technologies such as digital control systems, adaptive control algorithms, and communication interfaces. These advancements aim to improve the overall performance and reliability of the excitation system.
The excitation system’s performance is often evaluated based on various parameters, including voltage regulation, transient response, voltage recovery after disturbances, and the ability to provide reactive power support.
Excitation systems are not limited to synchronous generators used in power plants. They are also employed in other applications such as synchronous motors, synchronous condensers, and certain types of industrial machinery.
In conclusion, the excitation system of a synchronous generator is a complex arrangement of components and control mechanisms that ensure the generator operates at the desired voltage and reactive power output.
It is responsible for regulating the field current to maintain a stable magnetic field in the rotor. The excitation system plays a crucial role in power system stability, voltage control, and synchronization.
- Excitation Systems: Components & 4 Important Methods
- Automatic Stator Winding Machine: Best Guide
- Induction Motor: Important Types, Construction & Working
- What is Demand Factor and Diversity Factor? Quick Concepts
- Power Triangle: Best Applications You Need to Know
Subscribe to our Newsletter “Electrical Insights Daily” to get the latest updates in Electrical Engineering. You can also Follow us LinkedIn and Facebook to see our latest posts on Electrical Engineering Topics.